Last Updated on
There are many types of a thermostat in the market these days. If you are looking for a good quality thermostat wiring heat pump then please try to check properly that thermostat before buying. A good quality thermostat wiring you can buy around less than 50 dollars.
Usually, in the United States, AC power supply powered by 24V which comes from a 110V/24V power transfer.
If you are not a qualified technician then I would say try to get a qualified technician who can do it properly.
Heat pump thermostat wiring Tips
Some Heating, Ventilation, and Air conditioning expert called HVAC experts to use several colours for additional control points. So these diagrams and charts will represent the basic System. That is why we will suggest you read the manufacturer’s instructions. Everything will depend on manufacturers and designers of the components. How these components integrated into the system.
Before uninstalling the thermostat try to take a picture of wires to your cell phone. This way you have good support to wire thermostat. That picture can help you to make sure while you will joining it in the new thermostat correctly.
The post meant the following guide only. Always try to follow manufacturers’ instructions for both thermostat and HVAC Systems. Additionally, this article will help you to solve the problem thermostat wire properly.
The Basic thermostat wire colours
- R red wire is the R terminal connect to 24V AC power
- G green wire is the G terminal connects to the indoor fan
- W white wire is the W terminal connects to the heat
- Y Yellow wire is the Y terminal connect to cool
- C black wire is the C terminal connect to 24V AC Common
- O Orange is the O terminal connect to RV on in Cool
- B Blue is the B terminal connect to RV on in the heat
When it comes to the Honeywell thermostat wiring heat pump, you are wiring the heat pump thermostat over to the indoor wire handler you going to typically run 18:8 thermostat wires. You can run 18:10 thermostat wire which gives you additional wires for a potential outdoor sensor.
The Thermostat colour code for the heat pump thermostat over to the indoor air handler. That is why Yellow and G compressor that green and that’s for the fan. Otherwise Red that’s for 24-volt power, C is blue and that’s common for 24-volt power.
E is typically white and E is emergency heat. Aux, in this case, hampered over to E and Aux mean Auxiliary heat. O is orange and that’s for the reversing valve that leaves two additional wires, one is black, and the second is blown.
You can use it in case there’s a problem in the future. The thermostat wire that you want to run from the air handler to the heat pump is typically going to be 1816 or 18:8 water. In this wiring diagram, you will see that and you will use only 5 wires. So if you are an 18-6 wire and you are going to have an additional wire to be safe for the future.
In case, you need to change one of those wires out. If you have an outdoor temperature sensor that ends up finding its way all the way back to the heat pump thermostat you need to run to additional wires from the air handler to the heat pump.
So that means you would end up having to run eighteen eight wire. So powers going to originate at the handler control board and then it’s going to move on from there. So the power goes from the air handler board over to the heat pump thermostat. It connects to the load of the heat pump thermostat.
In order to turn a digital display on and it finds to way back through the common wire over to the air handler control board. You can hardwire that heat pump thermostat or you cannot wire up the C terminal and just use the batteries in the heat pump thermostat also the indoor air handler board. Also, the outdoor heat pump has to those as well.
If you are going to turn the air conditioner on at the heat pump thermostat or going to send 24 volts over to the G to the Y into the terminals. Then the 24 volts are going to be over on the air handler control board on the Y and G terminals and also the O terminal and then it’s going to continue to make. Its way outdoor heat pump on the Y terminal and the reversing valve O terminal. So that’s going to turn on your outdoor heat pump on air conditioning mode. So it’s going to control the compressor.
While you turn on it the heat pump thermostat says at 70 degrees inside the house or inside the building. You turn it up to 71 degrees what’s going to happen is the terminal? It is going to send 24 volts over to the G and also the Y terminals in the heat pump thermostat. The 24 volts is going to make it over to the indoor air handler. The G terminal has 24 volts on. It’s going to tell the blower motor to turn on as well.
You can have the 24 volts on the Y terminal at the air handler then you can also send volts out to the heat pump to turn the compressor on. In this case, you have to reverse the valve with no power heat pump. So, the outdoor pump is running and the indoor air handler is running.